APPROVED – for use in CALIFORNIA ( other popular brands are NOT approved for California !, EG4 etc)
American Certification Standard: UL2271 UL2054 UL1642
This is a premium product!
We are trying to help customers get prepared for what is shortly to come, if you don’t know what I mean, then this isn’t for you. (One day everything will STOP, yes the signs all all over, and its happening faster than anyone can imagine)
* Free Shipping Conditions. (While stocks last)
Order 3 or More PYTES along with ANY other products, we will palatalize shipment and send to the closest Lower 48 FedEx freight terminal (for pickup) , if you have a business address with forklift / loading dock, we may be persuaded to send it there too.
The closest FedEx fright terminal is shown on the first Checkout Screen where shipping options are calculated, you can paste this address into the additional notes field or any other comments on the checkout comments
This deal cannot be offered with any other coupons.
USE CODE “PYTESDEAL”shipping will be removed on checkout screen if more than 3 batteries are in your cart
Finally, a battery that stands up to the task.
UL1973-2018, CEC, UN38.3, UL1642 Certified
Double Redundancy Texas Instruments chips used on BMS main-board
Expandable to 72kWh in a single system. (12 pcs)
10 Year Warranty 6000 Cycles 90% DOD , the most flexible battery protocol
Residential Energy Storage System
Battery 4 AWG Interconnect & CAT5 Cables included
Click Link Here for PDF Resources Manuals, Specs ,Warranty
Quick GroWatt Inverter Configuration instructions.
On Battery set dip switch #3 UP, all others DOWN
Communication Cable: available here (One cable required per Inverter)
- Plug in PYTES / Growatt Communication cable marked “Battery” into Battery Can Bus Port
- Plug in end marked “HUB” into Growatt CANBUS port,
- Do the above for each inverter connected in parallel to the same battery cluster
Set battery type (setting 05) to LI
and Protocol to be L51 (Setting 34 , immediately follows from above)
If the Inverter does not supply AC power after the above, set setting 05 to AGM , and retry settings above.
Troubleshooting: Fault 20 indicates communication failure, Fault 04 = low battery
NOTE: Inverter will not output 120V if BMS communication is lost (and battery type is set to LI)
Quick MPP Solar Inverter Configuration
On Battery, set dip switches on each battery according to the address ,E.g. First battery, all down, 2nd – 1 up, 3rd – 2 up, 4th – 1 & 2 up, 5th – 3 up, 6th – 3 & 1 up, 7th 3 & 2 up, 8th 3 & 2 & 1 up
Communication Cable: available here (One cable required for one inverter communicating with the battery)
On ONE Inverter with cable connected (connect end marked “Battery” into Battery “Serial” [= RS485 Port- –NOT the CAN Port], End Marked “Voltronic” into Inverter Battery port)
On inverter with battery communications cable connected Set battery type (setting 05 on LV6548) (setting 14 on LVX6048) etc to “PYL”
On all other inverters connected in Parallel, set battery type to “USE”
Fault 61 on the LV6548 indicates battery communication failure
On the LVX6048, a warning beep sound along with the fault LED
NOTE: If all is working, the battery ICON on the LV6548 will flash, on the LVX6048 a flashing battery outline indicates BMS communication
Comparison sheet PYTES – to SOK / EG4 See Product Images